SES 3,996 MW "Borki-2"
Start generated: 12.2019
1 Type of
- The installed capacity of PV modules— 4,63 MW;
- Inverter the power station— 3,9 MW;
- The volume of annual generation of electricity— 5848 MW/year;
- Reduction of CO2— 3362,6 tons;
- The number and capacity of polycrystalline solar panels "Talesun" - 14 PCs. 060 x 330 W;
- The number and power inverter "Fronius" — 148 pieces x 27 kW;
- Number of transformer substations - 1250/10/0,4 - 2;
- Number of transformer substations - 1000/10/0,4 - 2;
- The number of load-bearing steel structures 38
- The number of distribution substations of 10 kV DP - 1 PCs;
- The conversion of solar energy into электрическую10000 W, 50 Hz and its transmission in the power grid to other consumers
A bidirectional counter:
- on networks generation SL 7000;
- for my own needs – ACTARIS ACE6000.
- Feasibility study (FS);
- Development of project documentation;
- Supply of solar panels and inverter equipment;
- Supply of power and electrical equipment;
- Construction and installation works;
- Connection built SES to the network;
- Registration of membership in the wholesale electricity market and approving "green" tariff;
- Service SES.
AC: 10 kV:
- vacuum circuit breaker 35 kV ВР35НСМ-35-25/1600A (rzva);
- the surge of Apnp-10;
- the VVC 2АПКН fuses 12kV 10 kV;
- current transformers TOL-10 10P/0,5/0,5 S/150/5;
- voltage transformers - NTAMI-10.
In the operation of solar power plants:
- you must comply with the conditions and requirements for operation of equipment provided by manufacturers in the relevant instructions;
- before switching on the equipment, you must ensure in absence of mechanical damages;
- it is advisable to periodically carry out maintenance according to the recommendations of its manufacturer;
- it is necessary to strictly comply with the relevant security measures.