SPS 975 kW "Grebinka"
Power: 975 kW
Area: 1,8 ha
1 Type of
- Installed capacity of photovoltaic modules — 1,175 MW;
- Inverter capacity of station – 0,975 MW;
- The volume of annual electricity generation is 1503 MW/year;
- Quantity and power of polycrystalline solar panels "JAM 72S09-380 / PR" - 3094 pcs. (380 W);
- Quantity and power of HUAWEI SUN2000-36KTL inverters - «SMASHP75-10» - 13 pcs .х 75 kW;
- Number of load-bearing steel structures - 92 pcs;
- Complete transformer substation -1250-10-0,4-У1 - 1 pcs.
- Conversion of solar energy to ~ 10000 V, 50 Hz electric power and its transmission to the electricity grid to other consumers.
Accounting for electricity:
- on generation networks - SL ZMD 405+С32:С40 СГ 44.557 С;
- on your own - GZMG 310.
- Feasibility study design;
- Development of the design documentation;
- Supply of solar panels and inverter equipment;
- Supply of power and switchboard equipment;
- Construction and installation works;
- Connection of the constructed SPS to the grid;
- Member registration in WEM and “green” tariff approval;
- Service maintenance of SPS.
0,4 kV and 10 kV AC power supply:
- automatic air switch 10 kV BB/VL12-25-1000A ;
- surge suppressors - ОПНп-Ю/12,0 ;
- РВЗ10-630-11 fuse disconnector;
- П Т 011-10 fuses.
- current transformers ТОЛУ 10 75/5 (ABB);
- voltage transformers ТШ 066-2/1500 5А.
When operating a solar power plant:
- the conditions and operating requirements of the equipment provided by its manufacturers in the relevant instructions must be observed;
- Before switching on the equipment, make sure that it is not mechanically damaged;
- it is advisable to periodically perform maintenance work on the equipment as recommended by its manufacturer;
- Appropriate safety measures must be followed.